Trying to get the receptacles to not be dim-able or switch-able and lights to switch and/or dim in a new home built in 1927. Please refer to the picture. A bunch of weird behavior and hoping someone can here can decipher and explain what I'm seeing. Help is greatly appreciated.
The switch controls the receptacles. The switch and dimmer combined will dim the ceiling lights and the receptacles.
The ceiling lights turn on but dim when:
* Anything is plugged into one specific receptacle and the dimmer and the switch is on
The ceiling lights go from barely lit to dim and lights plugged into the receptacles also dim
* When toggling the dimmer, the switch is also on, and anything is plugged into one specific receptacle
The receptacle tester (GB non-GFCI) reports all 3 lights (red/y/y)
* When white is connected to silver and black to bronze
The receptacle tester reports 1 red, 1 yellow (reversed hot/neutral)
* When white is connected to bronze and black to silver