Fri 29 Apr, 2016 07:33 am
I have a high and low voltage problem, I disconnected the panel from the meter connected to Comeds side of the meter hot and neutral. As I put a load on the lines one leg drops from 124v to 108v while the opposite leg raises from 124v to 140v
Sounds like you have a high resistance in the common path. Corroded connection or something like that.
By common, I mean somewhere in the neutral path.
Right that's what I was thinking, just waiting for the utility company to come out to prove it to them. Thanks
High resistance in the common path, Resistance is the measure of opposition to electric current.